For a printable version of this case study click here.
Chart Inc. is committed to providing its customers with the best cryogenic equipment solution for their specific application and offers within its extensive product lines the VSCO2 Vertical Bulk Station with Vacuum Composite Super Insulation™.
Oxygen Service Company (“OSC”) is a welding supply company covering the majority of Minnesota and Wisconsin from three Minnesota locations. It is 100% employee-owned and carries a full line of welding equipment, supplies, industrial and spec gases. The company philosophy is to offer the highest level of service to all of their customers.
OSC was using around 20 tons of CO2 per month and storing it in a 40 year old Cardox 24-ton horizontal tank with foam insulation cooled by an external refrigeration unit. The tank’s foam insulation had degraded from water saturation to a point that the chiller (3.5 kW) was running whenever the unit was not in use, nearly 150 hours per week. In addition, the Freon® refrigerant for the old chiller was costing around $350 per year to maintain.
Provide a more efficient Bulk Carbon Dioxide storage tank to reduce their expenses for electricity and refrigerant maintenance.
Replace the old foam tank with Chart’s VSCO2 30-ton Vertical Bulk Station utilizing Composite Super Insulation and superior vacuum technology. This unit offers ultra-low heat leak, eliminating the need for a costly refrigeration system with no down time compared to refurbishing the deteriorated foam. This proven technology provides all the benefits of bulk storage with no gas losses between refills, with a minimum usage of .08%/day (48 lbs/day) in the 30-ton model.
Among the many benefits of the Chart VSCO2 Standard Bulk Station over foam-insulated tanks are:
By eliminating the need for an internal refrigeration coil and an external chiller, OSC was able to save $230 per month in electricity costs (3.5 kW @ $.10/kWh) and about $350 per year in Freon service costs. This adds up to an annual savings of $3,110 per year.
Old System: Cardox 24-Ton Foam Insulation (1974)
New System: Chart 30-ton Standard VSCO2 System
“The new Chart bulk CO2 tank keeps our liquid pressure lower than our foam tank, even without a refrigeration unit. This helps our pump cool down faster, saving us time on start-up. The savings from electricity and maintenance provides us an excellent ROI. Overall, the Chart super insulated tank is a solid investment that looks great today and will be for years to come!” -Trevor Kelsey, Specialty/Industrial Gas Plant Manager, Oxygen Service Company